10ton Containerized Direct Cooling Ice Block Machine for Tropic Countries
|FOB Price:||Get Latest Price|
|Min. Order:||1 Piece|
- Model NO.: QZB-10T
- Cooling Way: Water-cooled
- Unit Structure: Integral
- Ice Temperature: -5℃~-10℃
- Application Fields: Aquatic Fishery
- Condition: New
- Transport Package: Containerized
- Origin: Zhejiang China
- Ice Making: Evaporating
- Automation: Automation
- Machine Size: Medium
- Ice Shape: Ice Block
- Certification: ISO, CE
- Trademark: KINGFIT
- Specification: 40FT Container
- HS Code: 84186990
Containerized Directly Cooling Style Block ice machine:
As conventional way to produce block ice is mainly from brine system, first you have to freeze the brine water, then put the ice can into the brine tank, then take out the ice can for harvesting block ice after 20 hours or more. This system is complicate and you have to do a lot of civil work. Our new system is using aluminum plate as ice can, the refrigerant will be evaporated inside the aluminum plate so the plate can freeze ice making water quickly.
One more thing, we supply compact ICE MACHINE which will be tested well Before shipment, it is plug-ready and build for tropicalconditions and coastal climate . the buyers can install all system by themselves without any promble.
Basic design parameters:
* Max. air temperature 50°C
* Ambient wet bulb temp. 50°C
* Ambient dry bulb temp. 43°C
* Water temp. for ice 16°C
* Relative humidity 90%
* Block ice plant for tropical use.
* Aluminum alloy as ice cabinet
* Block weight 20kg
* Refrigerant be used R22.
Brand new ISO container constructed according to ISO:
The main frame strength and corner fittings of the container are constructed of welded steel parts, which are protected against corrosion by hot dip galvanized.
The sides, roof and end walls are made of 50MM PU glass reinforced plastic insulation panel density 45 KG/M3.
The floor must be of adequated corrosion resistant aluminum chequered plates.
One stage reciprocating compressor, open or semi hermetic type connected with electric motor. The compressors are equipped with:
Section and discharge stop valves,
Oil level glass,
Equipment for unloaded start,
Electric heating rod in crankcase,
High suction and oil pressure gauges,
Safety cut out for compressor and discharge temp.
High low and oil pressure cut out,
Oil separator with solenoid valve controlled oil return,
None return valves.
Air cooled condenser provided with copper fins (cu/cu) mounted outside the container.
The capacity of the condenser should be based on an ambient dry temp +45°C and the condensing temp+45°C.
Condenser should be able to use for:
Low discharge pressure and condensation temp.
Highly economic way to increase the efficiency and to decrease the power consumption of the plant.
(4) ELECTRICAL PANEL:
Switch and control panel insulated in stainless steel board execution for three phase 380 volts. 50 Hz provided with the following accessories:
Star-delta starter for compressor motors,
Volt ampere and frequency meter,
Three phase failer relay
Indicator lamp for operation and faults,
Emergency stop switch.
(5) ICE MAKING PLANT:
(5-1) Brine tank:
This new system DOES NOT NEED any brine tank and chemical(NACL) water.
This new system is using aluminum freezing plate evaporator, the refrigerant will be evaporated inside the aluminum plate so the plate can freeze ice making water quickly.
(5-3) Ice cans:
Made of Aluminum alloy as ice cabinet for 20KG ice block each.
(5-4) Ice can frame:
(5-6) Thawing tank:
After freezing water into ice, hot gas from refrigerant unit will be injected inside the ice cabinet for having ice block down from the bottom.
Ice Capacity (kg/24hrs)
Aluminum freezing ice cans
32blocks * 2
Ice block size
Ice making time
Ice storage in container